Boiler Manuals for the Worcester Greenstar 24I Junior NG appliance. View and Download Worcester GREENSTAR 24i junior instruction manual online . wall hung RSF gas-fired condensing combination boiler installation. View and Download Worcester GREENSTAR 24i junior instruction manual online . WALL HUNG RSF GAS FIRED CONDENSING COMBINATION BOILER.
|Published (Last):||8 July 2012|
|PDF File Size:||16.50 Mb|
|ePub File Size:||12.37 Mb|
|Price:||Free* [*Free Regsitration Required]|
To print the manual completely, please, download it. Connect the expansion vessel flexible pipe to the hydraulic manifold situated left of the pump. Disconnect the electrical connector from the diverter valve motor. Twitter YouTube Facebook Latest news. Flue Installation After cutting, the end must be square and free from burrs to prevent damage to the mm flue seals.
The boiler will lie at an angle to the floor to allow the boiler outer casing E to be removed. This kit can be used in conjunction with the optional filling loop 7 not sup- plied with the boiler. Also See for 24i junior Installation instructions manual – 76 pages Installation, commissioning and servicing instructions – 64 pages Instruction manual – 64 pages. Worcester Greenstar 12i System Instruction Manual 74 pages.
Worcester 24i junior User Instructions & Customer Care Manual
Comments to this Manuals Your Name. Don’t show me this message again. This boiler is only suitable for installing internally within a property at a suitable location onto a fixed, rigid non-combustible surface at least the same size as the boiler and capable of support- ing the boiler weight.
Boiler Connections F from the retaining bracket. Remove bottom panel by pulling it forward and off. Wall hung rsf gas fired condensing combination boiler 20 pages.
As you have already saved the maximum of 9 manuals to your online services account you need to delete one of these before you can save another one. Wall mounted combination boiler for central heating and mains fed domestic hot water 39 pages. Hang the boiler on to the wall mounting frame manal the two brackets positioned left and right at the top rear of the greenstaf. Wall mounted combination boiler for central heating and mains fed domestic hot water 36 pages.
WORCESTER GREENSTAR 24I JUNIOR INSTRUCTION MANUAL Pdf Download.
This manual also for: Flue Terminal Positions 50 mm around the flue and fixed to the wall with plated screws. Clean around sealing surface on sump and replace access cover P. Manyal the best energy tariff for you Get a quote.
Electrical switches, fused spur and socket out let s must not be sit uat ed in t he bathroom. Save energy Energy saving tips. In order to save this manual to your online services account please log in or register for an account. Submit a meter reading Your bill Compare my energy usage Book an engineer Moving home Keeping your account safe. How do I release pressure so red needle is set at 1half to 2 as at moment its 4.
Plumbing Manifold Further guidance on pipe routing can be found printed on the boiler template supplied with the boiler. Table of Contents Add to my manuals Add. This kit can be junoir in conjunction with the optional filling loop 7 not sup- plied with the boiler.
Answer a few simple questions to see whether it is a simple fix with no engineer required. Pull valve up and forward out of boiler. To refit, follow the above in reverse. Ensure any seals that have been disturbed are renewed.
Lift up assembly and remove from boiler. By pressing ‘print’ button you will print only current page. Wall mounted combination boiler for central heating and mains fed domestic hot water 36 pages. Juniod all windows and doors. Wall mounted combination boilers for central heating and mains fed domestic hot water 65 pages.
The boiler will be reset.
Undo the flue connection from the sump and push the flue tube up. If the boiler is not to be commissioned immediately then: A flow restrictor is fitted within the appliance which limits the hot water delivery rate to a maximum of 8.
Starting The Appliance Turn manal boiler thermostat control C to maximum. Replace expansion vessel and refit the boiler to the mounting frame. Page 37 Remove bottom panel by pulling it forward and off. Replacement Of Parts This is to allow sufficient time for the setting procedure. Complete the Benchmark checklist. Worcester cannot be held responsible for costs incurred by persons not deemed to be competent.