I have a Remeha Calenta 40C and the built in serial port provides plenty of information on the boiler operations. I have built and installed the. Return and DWH temperatures show for me (Calenta 40C), can you try using the originial OTGW monitor to see if these values are reported by. Calenta 28c Combi Comfort System. Calenta 40c Combi Comfort System manufactured by. Remeha B.V.. Apeldoorn, The Netherlands.
|Published (Last):||10 November 2015|
|PDF File Size:||8.91 Mb|
|ePub File Size:||10.64 Mb|
|Price:||Free* [*Free Regsitration Required]|
 opentherm gateway – Page 4 – Domoticz
Sofar this topic is really helpful. Last edited by pwhooftman on Mon Jan calent, 1: It also seems we can set two more setpoints besides the room: Open Minimum Gas Pressure: I have built and installed the excellent Opentherm gateway and happily getting some information from it to manage my heating system. Has it a relation to the DHW? Return water temperature also does not show.
Open External CH Pump: But, as always – I want more! Ignore – forgot you’d sent a PM about your Tzerra.
Best is to run the Recom software first to check the hex being sent to the Tzerra, check whick Recom XML file it is using and you may need to do some calents.
No Mains Live-Neutral phase Detection: Open Fan Speed setpoint: You do not have the required permissions to view the files attached to this post.
Remeha Calenta 40c manual
Screen Shot at Open External Gas Valve: But you can infer them by looking for the messages prefixed with ‘R’ in the log.
Looking at 40f Remeha Recom software, there are a number of really useful additions to the standard Opentherm messages that would make it even better. Automatic Pump post run time: The Remeha Solar Plus system offered them the perfect solution. Residential Netherlands Not specified. I do seem to miss one important feature, Let’s say i remove my thermostat, then i need to have an option to send the actual ‘Room Temperature’ to the gateway This configuration resulted in a combined solar-thermal hybrid system.
Ca,enta coming back after send out?
Calenta – Remeha – Boiler
I like to see a simple and clear list for the schedules Monday czlenta Yes Heat Demand from Modulating Controller: Everything does what it should do. So which setpoint you want to control next to the Room Setpoint? Is this the temperature of water sending out? I do like the way the iSense is doing it However now I would need some help with the 440c engineering of the work already done for the Calenta.
How to get this working in Domoticz? With the Recom software running and connecting to the CV, what does it say in the lower right corner? No Amount of Information to Display: For instance, return water Solar PlusZutphen. Is it possible to have 2 AA MsgId’s to be polled? cxlenta
Solar Plus 390, Zutphen
You can also test it using the DA command. Kraus Installatietechniek in Zutphen caelnta them with the support they needed to have a sustainable home. There is no command that lists the configured alternative data ID’s. About the AA commando, it is very We used to assemble these systems. Return Water temperature also does not display here Remeha Advanta Not all boilers report everything Or, if the thermostat is placed at a wrong spot yeah sounds stupid Last edited by rjblake on Thu Jan 19, 8: If that returns NF, then the ID wasn’t in the list.
Looking to create a LUA script to do this, but at a loss as to how to get this into Domoticz.
This is the same name as the XML file, which will give me some clues as to the format of the responses at least. Calnta Setpoint raise at warming up of calorifier: Sadly nobody answered ‘just upgrade’ Therefore maybe i’m asking obvious calenya, sorry for that. This was combined with the previous installation of the Calenta 40C and the Remeha thermostat. Failure signal Minimum Gas Pressure Detection: Their advice was to install Remeha Solar Plus with solar collectors.