Publication UMA-EN-P – November Table of Contents . User Manual UM to assign an IP address to the MicroLogix. controller. Publication INC-EN-P – October Important . Manual UM .. publication UM, for more information on surge suppression. rm_-en-p – Free ebook download as PDF File .pdf), Text File .txt) or read book online for free. Document Number IN UM
|Genre:||Health and Food|
|Published (Last):||6 December 2013|
|PDF File Size:||12.72 Mb|
|ePub File Size:||13.57 Mb|
|Price:||Free* [*Free Regsitration Required]|
1766-IN001 – Rockwell Automation
Do not drill holes above a mounted controller if the protective debris strips have been removed. Holding the controller, pry downward on the latch until the ne locks in the open em. Ensure that the battery 176 connector is inserted into the connector port if your application needs battery power.
Failure to remove strip before operating can cause overheating. This equipment is supplied as open-type equipment. If you would like a manual, you can: However, because of the variety of applications and environments where analog controllers are installed and operated, it is impossible to ensure that all environmental noise will be removed by the input filters.
Identifies information about practices or circumstances that can lead to personal injury or death, property damage, or economic loss. Trademarks 166 belonging to Rockwell Automation are property of their respective companies. Follow these steps to install your controller on the DIN rail.
Output group to output group isolation Verified by one of the following dielectric tests: In no event will Rockwell Automation, Inc.
Use a static-safe workstation, if available.
Switching inductive loads without surge suppression can significantly reduce the life of relay contacts or damage transistor outputs. For more information, contact your local distributor or Rockwell Automation representative, or visit http: The controller can be mounted to ENx7. Outside United States Please contact your local Rockwell Automation representative for the return procedure. Additional noise immunity can be obtained by routing the cables in grounded conduit.
Specifically, this equipment is intended for use in clean, dry environments Pollution degree 2 1 and with circuits not exceeding Over Voltage Category II 2 IEC 3. When using spade lugs, use a small, flat-blade screwdriver to pry the finger-safe cover from the terminal blocks, then loosen the terminal screw.
No patent liability is assumed by Rockwell Automation, Inc. AC powered products must be connected to the secondary of an isolating transformer. It must be mounted within an enclosure that is suitably designed for those specific environmental conditions that will be present and appropriately designed to prevent personal injury resulting from accessibility to live parts.
Plug the ribbon cable connector into the bus connector. Run the ground connection from the ground screw of the controller to the ground bus prior to connecting any devices. You must also provide an acceptable grounding path for each device in your application.
Mount your DIN rail. Use AWG 14 wire. Refer to the mounting template inside the back cover of this document. Reproduction of the contents of this manual, in whole or in part, without written permission of Rockwell Automation, Inc.
Wire the Controller The shading in the following terminal block illustrations indicates which terminal groups are tied to which commons. Allow 50 mm 2 in. Documents Flashcards Grammar checker.
The drain wire and foil shield must be grounded at one end of the cable. Because of the many variables and requirements associated with any particular installation, Rockwell Automation, Inc. Finger-safe cover TIP If you wire the terminal block with the finger-safe cover removed, you may not be able to put it back on the terminal block if the wires are in the way.
Wiring Hm001 Analog Channels Analog input circuits can monitor voltage signals and convert them to serial digital data as shown in the following illustration. Remove the mounting template from inside the back cover of this document. Follow these steps to connect the replaceable battery. Secure the battery connector wires so that it does not block the expansion bus connector as shown below.
Subsequent sections of this publication may contain additional information regarding specific enclosure type ratings that are required to comply with certain product safety certifications. The enclosure must have suitable flame-retardant properties to prevent or minimize the spread of flame, complying with a flame spread rating of 5VA, V2, V1, V0 or equivalent if non-metallic. When the ym001 is low, the indicator is set displayed as a solid rectangle.
A flat-blade screwdriver is required for removal of the controller. Each product is supplied with markings on the rating nameplate indicating the hazardous location temperature code. Several specific steps can be taken to help reduce the effects of environmental noise on analog signals: Follow these guidelines when you handle this equipment: Hook the top slot over the DIN rail.
Without appropriate precautions, there may be potential difficulties ensuring electromagnetic compatibility in other environments due to conducted as well as radiated disturbance. Repeat steps 1 and 2 for the second DIN rail latch. Be sure that power is removed or the area is nonhazardous before proceeding. Use a power supply that matches the transmitter specifications as shown.
IN – Rockwell Automation
Make sure that the placement of the controller on the DIN rail meets the recommended spacing requirements see Controller Spacing on page 12 for more information. Once wiring is complete, remove protective debris strip. Drill holes through the template.